Welcome back to Kung Fu maintenance! Wanted to let you know, show you, about one Ihad the opposite day. What happened was proper at the end of theday I noticed that there used to be a work order for a no heat call. Went and checked it out. The hydronic valves had been turned off and turnedthose on. Came visiting to the thermostat and became iton but nothing became on.I could see. The flame signal here. Very like this one. Now usually while you do it you’re going to hear thelittle click on when it turns on. On that certain one I did hear the clickand that type of signified to me that the thermostat used to be working. I grew to become the fan to on. The fan kicked on. I became the A/C on and the AC kicked on.Grew to become it to chill and auto. Diminished the temperature down and everythingkicked on there correct away. So I knew at that factor that it wasn’t theservice door change. Didn’t be aware of what it was however what I did waspullk the duvet off. Now earlier than I do that I want to exhibit you thelittle click on. I will lift my temperature up so the heaterwill activate a bit of bit. You hear that click on? That is signifying that my unit is gettingready to stir up because the heater has now been signaled to activate. However beneath. I’ll show you right here. What you may have bought is your pink bloodless jumperand the purple scorching jumper wire. That fatter red wire that’s again there.I bought variety of fortunate and observed right awaythat the insulation phase, even so much adore it is right here, the insulation component used to be up insidethe screw port. So All I had to do was once loosen the screw alittle bit. Transfer the wire down a tiny bit in order that thewire was absolutely making contact with the screw port so we’d have continuity. And that’s all it used to be. The screw alternatively of clamping the wire downwas clamping the insulation down. Insulation used to be making contact so that theheater wasn’t turning on despite the fact that it was once sending the call for warmth from the thermostat. It wasn’t being transmitted by way of the hotwire so. First-class convenient fix.Concept i might show it to you guys. Hope it saves you some concern.You already know. It is infrequent but these are the matters that happenand a little bit bit on the troubleshooting that happens. Certainly if a wire will not be making contactthere things are not going to activate. And one thing more I had checked on thiswhich must be checked when a thermostat is not working. One thing to investigate on theses is the jumperpin or the switch setting. This one has a bit of switch down right here whereright is for gasoline heating and left is for electrical heating. That specific one was once set for electrical heatingwhich is common to all of my different items for hydronic heating.So it wasn’t that. So once more it used to be that insulation that used to be blockading. In order that the wire wasn’t making contact onthe RH wire. Anyway. Thanks for staring at!.